Recently one of my YouTube channel subscribers asked an interesting question. He asked me that how he can connect a 3-phase motor protection circuit breaker (MPCB) to a single-phase motor?
Can we do that, is that possible?
Yes, but with word of caution.
Check out this video to understand and see the inside view of the circuit breaker.
Here. I will give you step by step guide to connect 3 phase MPCB to a single-phase motor.
How to connect 3-phase motor protection circuit breaker to single phase motor?
Step 1: First connect the live wire to L1. Look at the below image.
Step 2: Then connect the neutral wire to L3.
Step 3: Now connect the motor wires to the T1 and T2 terminals of MPCB.
Step 4: Finally, connect a wire from L2 to T3 of MPCB.
In a single-phase circuit, neutral acts as a return path.
You know that – right?
So, we must do a connection such that all three poles of the motor protection circuit breaker come under the loop.
Take a look at the below image. The two poles of the motor protection circuit breaker are in series.
In this way, you can run a single-phase motor with 3-phase MPCB.
Make sure that now you adjust the range of MPCB as per motor nameplate current ratings.